RGP-GZFB-2011A The 12 Port FC Fibre Patch Panel is designed for space-saving and high-density applications. The patch panel is made of 16 gauge cold rolled steel(CRS) with a black or grey powder-coated finish. Equipped adopt removable back cover, it allows a simplified from access, inside-panel manipulation, and splices.
FC, SC, and LC adapters available, modular design, convenient for fixation and maintenance.
Buy Fiber Patch Panel (Rack Mount /Wall Mount, Fiber Termination Box, 12-96 Fibers, LC/SC adapter ) for Fiber Distribution Terminal from reliable fiber optic supplier-MJADOM.COM
High quality sheet metal material, electrostatic spraying treatment on the surface, good mechanical performance, Elegant appearance, robustness and durability.
Suitable for indoor ,wall-mounted installation.
FC, SC and LC adapters available , modular design, convenient for fixation and maintenance.
Standard color is RAL 9005 black ; RAL 7035 light grey is also available.
Cable clamps on the inner surface for fixing cable.
Front and back flexible wire guard.
Installation hardware and instruction manual included.
Built-in stacked splice trays, easy to open, the splice tray can be taken down, easy for installation and maintenance.
Pigtail fastened by imported elastomer, fixed reliably and convenient for use.
Offer fixing devices for cables, pigtails, and grounding device inside the box.
Fibre route reasonable, fibre bending radius at any place is greater than 30mm.
Operating temperature: -5℃～+40℃(Indoor type),-20℃～+60℃(Outdoor type).
Ambient humidity: ≤95%(+40℃).
Atmospheric pressure: 70 kPa～106 kPa.
Insulation resistance: not less than 2 x 104 M Ω / 500 V (DC).
Withstand Voltage: not less than 3000V（DC/1min.
Insertion loss (dB): ≤0.3dB.
Return loss (dB): PC type≥45dB, UPC type≥50dB, APC type≥60dB.
Datacenter & Central Office.
Cellular tower base station.
LAN & WAN projects.
Complied Standards :
Meet national standards, such as YD/T925-2009, GB/T2423-2008, GB/T3873-1998, GB/T 9286-1998, and international standards, such as IEC 61300-3-15, IEC 61300-3-16, IEC 61300-3-17, IEC 61300-3-23, etc.