MJADOM offers a range of overvoltage protection/protective unit for the LSA-PLUS/LSA Profile series 2 Connection and Disconnection modules, in the form of plug-in magazines fitted with 3-pole Gas Discharge Tubes(GDT), In addition to the primary protection afforded by the GDT, additional thermal fail-safe functionality may be fitted, to protect against overheating from interference currents, E.g. power crossing.
The overvoltage protection devices are inserted fully into the contacts of the Connection or Disconnection module, ensuring that the clamps on the sides of the modules grip the lugs of the back mount frame or the earth clips of the profile rails, Connection to LSA PROFILE Disconnection and Connection modules and rails is via the earth contact clips.
MJADOM offers a full range of Krone LSA-PLUS Disconnection Module & Connection Module & Highband Module & STG Module & Back Mount Frame and Gas Discharge Tube Protective Unit.
Gas discharge tube adopts IDC (Insulation Displacement Connection) design.
Flame retardant performance
Gas Discharge Tube Arresters Modular design and installation
Compatible with Krone disconnection module.
The 3-pole gas discharge tube surge protector will normally recover after a rated surge passes.
The optional fail-safe 3-pole gas discharge tubes will open the circuit to a fail-safe state if there is a sustained power surge.
GDT Gas Discharge tube Life: durability 500 cycles.
|Type||RGP-TSF-202A||Style||3 Pole Protection Magazine With Gas Discharge Tube|
|Capacity||10 Pair||Dimensions (HxWxD)|
|Insulation resistance||≥1000MΩ at 100VDC||DC spark-over voltage||180-300V|
Impulse spark-over voltage
Nominal arrestor alt.discharge current
Nomminal arrestor surge current
|5kA||Transverse time(1Kv/μs)||< 200ns|
|Fail-safe response time||5s(5A)|
|Storage temperature||-40°to +80℃||Operation temperature||-20°to +60℃|
|Relative humidity||≤ 93% non-condensing||Environment for use||Indoors, in dry closed rooms|
Main distribution frames of exchanges.
In cross-connection cabinets and terminating boxes.
In building entrance distributors.
In-floor distributors or in PABXs for voice and data distribution.